The main problem when installing a multi-split system is the laying of long refrigerant lines for connecting the external unit to the internal ones. While installing a separate split system, workers try to locate both units opposite to each other, where the length of the line is minimal. Installing a multi-split system creates more difficulties, since some of indoor units can be located far from the outside. The first models of multi-split systems had one common control system that did not allow you to set the air conditioning individually for each room. However, now the market has a wide selection of multi-split systems, in which the functional characteristics of indoor units operate separately from each other.
An air conditioning system, or a standalone air conditioner, provides cooling and humidity control for all or part of a building. Air conditioned buildings often have sealed windows, because open windows would work against the system intended to maintain constant indoor air conditions. Outside, fresh air is generally drawn into the system by a vent into the indoor heat exchanger section, creating positive air pressure. The percentage of return air made up of fresh air can usually be manipulated by adjusting the opening of this vent. Typical fresh air intake is about 10%.
Replacing your old heating and cooling equipment with new, energy-efficient models is a great start. But to make sure that you get the best performance, the new equipment must be properly installed. In fact, improper installation can reduce system efficiency by up to 30 percent - costing you more on your utility bills and possibly shortening the equipment's life. Learn more.
Our heater went out last Saturday, which was a cold day. Called a few different places and they… Our heater went out last Saturday, which was a cold day. Called a few different places and they were the only ones that called back. The technician Tony came out and after a little testing said the main control board needed to be replaced. He quoted us a total of $489 which seemed on the high side but it was cold and we were somewhat desperate, so we agreed and paid a parts deposit.
If your compressor doesn’t have an overload button and you hear it humming or buzzing, poke a screwdriver or stick down through the top grille and try to spin the fan blades clockwise. If doing this gives the fan enough of a boost to get it going, the unit has a faulty capacitor that must be replaced. See How to Test and Replace an AC Run Capacitor, above.
"Our Pro was the most courteous and informative gentleman that we have had the pleasure to work with, was great. He let us know immediately what the problem was and what the cost to fix it would be. Also, he let us know how to maintain and extend the life of our washer. He was very personable and made us very comfortable with the process. We would have him back in a heartbeat if anything ever goes wrong again. It was the best experience we have ever had with a appliance repair service."
The contactor (relay) and start/run capacitor(s) (see illustration below) fail most often and are inexpensive. So it’s a safe bet to buy and install those parts right away, especially if your air conditioning service unit is older than five years. The condenser fan motor can also fail, but it runs about $150 — hold off buying that unless you’re sure that’s the culprit.