Some systems include an "economizer mode", which is sometimes called a "free-cooling mode". When economizing, the control system will open (fully or partially) the outside air damper and close (fully or partially) the return air damper. This will cause fresh, outside air to be supplied to the system. When the outside air is cooler than the demanded cool air, this will allow the demand to be met without using the mechanical supply of cooling (typically chilled water or a direct expansion "DX" unit), thus saving energy. The control system can compare the temperature of the outside air vs. return air, or it can compare the enthalpy of the air, as is frequently done in climates where humidity is more of an issue. In both cases, the outside air must be less energetic than the return air for the system to enter the economizer mode.
When the mercury is rising or the frost is starting to form on the inside of your windows, you don't want to wait. You want your comfort restored without delay. So do we! That's why we provide emergency HVAC repairs 24 hours a day, 365 days a year. ARS/Rescue Rooter specialists are highly qualified, trusted professionals who are background checked and drug tested, so you can rest assured that our work is not only fast—it's also backed by our Exceptional Service Guarantee.
Are there watermarks on your ceiling? Visible leaks around your outdoor unit? Has your AC system completely stopped working? If you notice any of these signs, it’s in your best interest to call an AC technician to fix the issue before it causes more problems for you, your AC system, and your home. To learn more about potential AC malfunctions and how we fix AC issues, visit our AC Repair page.
Looking to cut down your home heating and cooling costs? Trane TruComfort™ Variable speed systems do just that. Trane TruComfort™ runs at the speed necessary to keep your home continuously comfortable – automatically adjusting up and down within one-half degree of your setting and constantly circulating air. The result? Running at up to 21 SEER (Seasonal Energy Efficiency Ratio) – which means affordable residential heating and air for you.
Our skilled technicians arrive prepared to handle the scope of even complex malfunctions, with all makes and models of heating and cooling equipment, most often resolving the problem on the spot. For all your HVAC service, repairs, and installations in Livermore, CA, Pleasanton, CA & Dublin, CA, call the team from Miller’s Air Conditioning & Heating!
We believe in building trust and bringing you value for every dollar you spend. Our proven Enhanced Services Program does just that, providing all of the benefits of a full service maintenance program with none of the draw backs. Our transparent process has no pre-existing issue limitations, no equipment or component exclusions, and ensures you receive value for every dollar of your budget.
Call Miller's Air Conditioning & Heating at (925) 583-6387 and always speak with a live and helpful member of our team, who will immediately focus on your requirements. While our competitors punch a strict time clock, we realize heating and cooling challenges often arise outside of regular business hours. Rather than leave a message on a machine, take advantage of personalized service and the prompt response of radio dispatched trucks.
They were quick to come out and diagnose the problem with my furnace, but I thought the estimate of $549 a bit high to replace the circuit board. So called around and found Leo's Appliance in Concord that sells appliance parts and the circuit board was only $90.49 - that is the retail cost to me, so I imagine the wholesale cost is a lot less. So BEWARE of this company since they wanted $500!!! to replace the circuit board which is located right in the front of the furnace - extremely easy to access. I hate it that you cannot trust repair companies.
If you believe that the ac not working or you’re getting little or no cold air, check these three things first. Make sure all the registers in the house are wide open. Then be sure the furnace filter is clean. Then go outside and clean off the condenser coils (Photo 2). If several registers were closed or the filter was clogged, the reduced airflow could have caused the evaporator coil to ice up and stop cooling your home. If you’ve changed the filter and opened all the registers and you’re still not getting airflow at the registers, deice the A-coil. Move the thermostat mode switch from “Cooling” to “Off” and move the fan switch from “Auto” to “On.” Let the blower run for at least 30 minutes or until there’s good airflow at the registers. Then turn the AC back on to test it. If it works for the next 12 hours, you’ve solved the problem.